Ultra-low Emission Technology-Kaidi High Efficiency Graded Composite Desulfurization Tower Technology
(For ultra-low emission of medium and high sulphur coal)
Kaidi High Efficiency Graded Composite Desulfurization Tower is a new generation of ultra-low emission technology developed by Kaidi independently and with full independent property rights. Aiming at the ultra-low emission of medium and high sulphur coal, this technology adopts graded graded composite desulfurization technology, uses different PH value absorbents and different mass transfer equipment in different areas of the desulfurization tower, and uses gas-liquid mixtures. The tray and spray layer are used as the mass transfer equipment at the front end of the contact, and the difference between the high concentration of the gas phase pollutants and the low concentration of the liquid phase is used as the mass transfer impetus to absorb most of the pollutant loads. At the same time, the lower pH limestone slurry is used to obtain better oxidation effect and gypsum quality. A new type of gypsum is used at the end of the gas-liquid contact. The high efficiency film liquid holding layer is used as a mass transfer device. The fresh limestone slurry with separate circulation is used as an absorbent. With its high pH value, the SO can absorb more fully and achieve deep desulphurization. At the same time, the new membrane liquid holding layer is used for foam washing to achieve high efficiency dust removal.
Under the condition that the sulfur content of coal is more than 2.4%, Kaidi high-efficiency and graded composite desulfurization tower technology achieves a single desulfurization efficiency of more than 99.5% and a sulfur dioxide emission concentration of less than 20 mg/Nm3. At the same time, compared with the tandem tower process, the stage composite desulfurization tower technology has significantly reduced the initial investment, operation energy consumption and operation cost.
On December 3, 2005, Huaneng Shanxi Zuoquan Power Plant's demonstration project of 600 MW desulfurization retrofitting for unit 2 was successfully operated for 68 hours. Under the operating conditions of 6000-7000mg/Nm3 concentration of S02 at the inlet of desulfurization flue gas, all indexes met the ultra-low emission standard.
+ High efficiency mass transfer internals are used to optimize the absorbent supply system, which reduces the equilibrium concentration of SO2, improves the oxidation effect and gypsum quality, and meets the ultra-low emission requirements of medium and high sulfur coal flue gas.
+ Load adaptive matching system can save energy and economy.
+ Optimizing the redistribution of absorbent in the column significantly reduces the liquid-gas ratio.
+ Perfect anti-deposition process system and monitoring system ensure long-term stable operation of the device.
+ Complete anti-deposition and scaling design ensures long-term stable and efficient operation of absorption tower.